Die Elektro-, Wasser- und Druckluftversorgung der Stände erfolgt in der Regel aus Elektroinstallation. Anschlüsse . Eine Errichterbescheinigung von . ausgabeaufschlag fonds beispiel hör elektro mannheim. sonderurlaub todesfall schwiegereltern momenti hofheim speisekarte Submitted by wie folgt aus. Elektro-, Wasser- und Druckluftversorgung im Freigelände. Errichterbescheinigung von der ausführenden Elektrofachkraft ist erforderlich, wenn.
|Published (Last):||12 February 2018|
|PDF File Size:||16.2 Mb|
|ePub File Size:||8.95 Mb|
|Price:||Free* [*Free Regsitration Required]|
HAUTAU RAZ K Rauchabzugszentrale |
Mortal danger by touching cables that are live. Smoke and heat exhaust ventilation systems must be serviced at least once a year by a specialised SHEV company with qualified staff and in accordance with all statutory regulations building code and state building regulations. Closing in the event of an emergency: Pull off the connecting plugs of the emergency power supply battery packs.
Check the central unit functions properly after successful installation of all components fire pushbuttons, smoke or heat detector, drives, ventilation pushbuttons, etc. Ensure a clear labelling of the wires of all components, which will be connected to the RAZ K, as well as the feeder wires of the power supply.
Bei Unstimmigkeiten informieren Sie umgehend den Lieferanten. H to connect the negative pole of battery pack! You absolutely have to observe the regulations of the professional association and state building regulations.
Check if all windows open and are opened all the way before closing the windows by pushing the Close button black in the fire pushbutton. The battery packs must be replaced no later than every 4 years. In case of power failure, the emergency power supply guarantees the operation of the SHEV facility for at least 72 hours. For larger cross-sections, reduce the cross-section immediately in front of the control unit.
The operability of smoke outlets, central units, fire pushbuttons, ventilation pushbuttons etc. Dispose of the battery packs in an ecologically desirable way acc. Finish by checking all functions as well as function and operation displays on the central smoke exhaust unit and the pivoting range of the drives. The clamping points in the control unit are designed for wire cross-sections of up to 2,5 mm2.
HAUTAU RAZ K Rauchabzugszentrale
Danger to persons due to electricity! The mounting of the control unit has to be performed by trained, qualified and safety-conscious electrical staff acc. If components have to be checked, repaired or replaced, please contact the manufacturer. Zentrale mit geeignetem Befestigungsmaterial an den vorgesehenen Bohrungen 9 befestigen. The inspection plate on the central unit must be renewed, and a control book must be kept.
When using a rain sensor, make sure to observe the current consumption of 0,5 A. Die VDE-Vorschriften sind zu beachten. The battery packs will have reached their full operating capacity after at least 10 hours of mains operation. Pay attention to earth the housing! F with negative pole of battery pack! Meldereinsatz entnehmen und reinigen. For the wires bore the housing exclusively at the corresponding positions at back!
The figures do not show items in their actual size and are also not of the same proportion. The wires are guided through the designated cable bushings from the top! It’s a community-based project which helps to repair anything. Manually by fire pushbutton, automatically by smoke and heat detector or third-party activation. All works at live components may be performed only by a skilled worker with completed professional training in the field of electrical equipment installation.
Never wire the components of the same loop in a star configuration. The control unit correspond with the actual standard of technology. Install the 10k terminal resistor color-coding brown, black, orange, gold used for line monitoring in the only or last smoke detector RM or heat detector TM OK according errichterbescheinigunf the terminal connection diagram.
After 16 minutes the ventilation is released. All smoke detectors actuate with smoke detector test control unit; the LED red on the detector is lit. Verwenden Sie geeignetes Befestigungsmaterial. If other drives are used, refer to terminal connection diagram next page. Ziehen Sie die Anschlussstecker der Notstrom-Akkumulatoren errichterbescheonigung. Please notify your supplier immediately in case of any irregularities. The red LEDs in the fire pushbutton and on the circuit board are lit.
A modification of connections is allowed only within the bounds of connection options. Two monitoring diodes 1N must be installed in the last conduit box in front of the drive and in accordance with the terminal connection diagram.