October Quick Start Guide for UDC Universal Digital Controller. For detailed instructions see UDC Controller Product Manual UDC Application Note. UDC AS AN AUTO/MANUAL STATION. SEVERAL CUSTOMERS HAVE LEARNED THAT THE UDC IS AN EXCELLENT. View and Download Honeywell UDC product manual online. Universal Digital Controller. UDC Controller pdf manual download.
|Published (Last):||20 September 2009|
|PDF File Size:||2.54 Mb|
|ePub File Size:||13.42 Mb|
|Price:||Free* [*Free Regsitration Required]|
Analog Inputs and Outputs: Both analog inputs are sampled six times per second every ms. Page – Radiamatic, Millivolts, Volts or Thermoc Page 94 Manual mode with the output set to the Output High Limit configuration. Figure and fill in the information for each segment.
LAN rather than using a Hub. Page 44 – Figure Position Proportional or Thr There are four alarm setpoints, two for each alarm. Using a Switch thus improves the overall throughput of the traffic to and from the UDCs.
Contact your local sales office for warranty information. Page 4 Chassis Ground. Are isolated from each other and all other circuits at Vdc for 2 seconds. Page of Go. Both Deadband and Hysteresis are separately adjustable. Restoring Factory Configuration The instrument configuration will now be the same as manuall was when the instrument left the factory and all user- entered configurations since that time have been overwritten.
These tags are fully explained in Section Page When the motor stops, the display should stop counting, then, go mannual Step 8.
HONEYWELL UDC PRODUCT MANUAL Pdf Download.
Table of Contents Add to my manuals Add. Installation instructions provided with new board.
The tag IDs represent the register addresses used in the Request Message. Installation instructions supplied with the new board. Algorithm Set Up Group hysteresis of the on and off states of each output. Opening the switch has no effect. Reopening switch has no effect. This section explains the operation of each selection and configuration reference where necessary. You will need the following equipment in order to troubleshoot the symptoms listed in the tables that follow: Page 2 Contact your local sales office for warranty information.
Page – Table Troubleshooting an Ethernet C This is the response to the above request. Controller Failure Symptoms In addition to the error message prompts, there are failure symptoms that can be identified by noting how the controller displays and indicators are reacting. Configure the values for: Table Mounting Procedure For water-protected installation, install four screws with washers into the four recessed areas in the corners of the front bezel Figure Selections are same as Same as above above.
Page 91 mA output operation without the need for recalibration of the instrument. Input 2 Set Up Group No other parameters are viewable. Monitoring And Operating The Controller 4.
See Figure through Figure Universal digital controller printed wiring board replacements 8 pages. Don’t show me this message again. Entering a 0 will imply an immediate step change in Setpoint i.
Page 98 If it is connected, only one instrument should run the loopback test at a manuql. Opening the contact will cause the Controller to revert to its original state. Connect a milliammeter across these terminals.
Alarm Setpoints Installation for alarm relay contact information. Limit Cycle Tuning with the objective of producing damped or Dahlin tuning parameters, depending upon the detected process deadtime. Don’t have an account?
The foregoing is Buyer’s sole remedy and is in lieu of all other warranties, expressed or implied, including those of merchantability and fitness for a particular purpose.
Range Value Units Input 2 Ratio — Customer should size fuses accordingly.
Honeywell UDC3200 Product Manual
Parts not manuwl are listed in Table The following formula applies: Alarm 1 is activated at the end of the timeout period. Use Fast Blo fuses only. Change a value To change any alarm setpoint value in the upper display. Radiamatic input signal that is the ratio of the actual energy emitted from the target to the energy which would be emitted if the target were a perfect radiator.